{ "items" : [
    { "id" : "http://webisa.webdatacommons.org/151613188"
      "properties" : {
        "http://www.w3.org/1999/02/22-rdf-syntax-ns#type" : [ "http://www.w3.org/ns/prov#Entity" ] ,
        "http://www.w3.org/ns/prov#value" : [ "Another thought on short cycling may be the anticipator or cycle rate setting on the stat. the high o2 number could also be due to a cracked heat exchanger i have not seen many gas units run a 6% o2 most of the time it is between 8-11%. what size is the flue pipe, could be oversized." ] ,
        "http://www.w3.org/ns/prov#wasQuotedFrom" : [ "hvac-talk.com" ] } },

    { "id" : "http://webisa.webdatacommons.org/prov/171998448"
      "properties" : {
        "http://www.w3.org/ns/prov#wasDerivedFrom" : [ "http://webisa.webdatacommons.org/151613188"] } } }
